CWCE FHBL 100W-200W LED High Bay Light Installation Manual
Views : 876
Author : CWCE Lighting
Update time : 2020-10-24 14:01:57
LED High Bay Light Installation Manual
-Mounting instruction for type Z.
-Terminal block not included. Installation must be performed by a qualified person.
-The exposed connected tails for dimming circuit were assessed as FELV,Installation must be performed by a qualified person. The dimmer connection at least IP20 in the junction box.
Wiring Diagram Terminal block not included. To ensure that the product meets the protection level requirements. The luminaire must be connected to terminal block with IP66 degree or above. The terminal bock shall be conform to IEC/EN 60998-2-1 or IEC/EN 60998-2-2 and has the below specification:- Screw terminal block with 3 holes- Suit for 1,0-2,5 mm2 wire connectingInstallation must be performed by a qualified person, brown wire must be connected L pole, blue wire must be connected N pole, yellow green wire must be connected earth pole.
LED lights have several advantages over traditional lights：
1)LEDs can emit light in a narrow band, which helps to produce a specific (sometimes adjustable) spectrum;
2)LED generates less radiant heat;
3)The LED has a longer working life;